Computer beige Seismic Frame® network rack supports 19 inch rack-mount equipment in areas with seismic activity. Network rack has a 7-foot high steel welded frame with tapped #12-24 zinc rails. Network rack is c(UL)us listed.
Seismic Frame® Network Rack, Two Post
CPI's SeismicFrame Two-Post Rack is specifically designed to support network equipment in areas with seismic activity.
The welded, steel SeismicFrame Two-Post Rack resists the swaying motion caused by earthquakes and reduces the amount of vibration transferred through the rack to equipment, so it is less likely to be damaged during a seismic event.
The SeismicFrame Two-Post Rack supports 19 inch EIA-310-D compliant or 23 inch wide equipment with two pairs of mounting rails that can be spaced 6 or 3 inches apart.
The mounting rails are marked and numbered with rackmount units (U) and are available threaded or square-punched with painted or zinc-plated finish.
This rack ships fully assembled and includes a Two Mounting Hole Ground Terminal Block for bonding the rack to the busbar.
The rack is rated for a 1,000 lb seismic Zone 4 load, per Section 4.4 of the Telecordia® Technologies, Inc. GR-63-CORE Network Equipment Building Systems (NEBS) requirements.
Welded, steel network equipment rack engineered specifically to protect equipment in areas with seismic activity
Vertical Powers Strips and T-shaped Cable Management Fingers attach directly to the rack channel to provide power and cable distribution for equipment
Fully bonded rack has (2) masked grounding locations and includes a Two Mounting Hole Ground Terminal Block for easy connection to the Telecommunications Grounding Busbar
Independently seismic-tested and certified, meets industry recognized Telecordia Technologies, Inc. GR-63-CORE Network Equipment Building Systems (NEBS) Zone 4 requirements
UL Listed NWIN per UL60950, File E227626
1000 lb (453.6 kg) load rating for seismic areas
Rack Includes: (1) welded, steel frame, (4) equipment mounting rails, (50) each equipment mounting screws/cage nuts and (1) Two Mounting Hole Ground Terminal Block